GENERAL EQUIPMENT INC.
8724 Sunset Drive #191● Miami FL 33173 · USA
18MW POWER PLANT
18MW Power Plant
As is, Where is
18MW power plant
From New Manufacture
PRODUCT PACKAGE DESCRIPTION
Industrial gas turbine KAWASAKI Model type L2OA
Horizontal split casing in industrial design, with openings for boroscope inspections.
Single shaft, entirely axial design, cold end drive.
11-stage compressor with transonic 1st and 2n,d stage, compression ratio 19:1, forged wheels,
electronic beam welded, forged single blades with dove-tail fixing, 1st to 6th stage Titan alloy, 7th
to 1 1th stage stainless steal alloy, abrasive aluminum coating of surrounding compressor housing
for minimum gap losses.
Automatic electric/hydraulic guide vane and stator vane angle adjustment on the first 5
compressor stages for Start unloading, mass flow control in part load and for DLE operation.
3-stage turbine, air cooling of entire 1st and 2nd stage with compressor discharge air, air
temperature reduction with pre whirl nozzles for turbine blades, film cooling, zirconium based
thermal barrier coating on entire 1st and 2nd stage, forged turbine rotors with curves couplings,
centre bolt, turbine blades of 1st stage made from directly solidified high temperature investment
casting nickel alloy.
2 journal bearings for radial load, 1 thrust bearing, all tilting pad type. Vibration and temperature
monitoring system, with 2 vibration transducers and 2 thermocouples on each radial Bearing and
1 position transducer on the thrust bearing. Exhaust gas diffuser designed with optimized opening
angle, inclusive temperature and back pressure measurement for the exhaust gas. Temperature
measurement performed with 16 sensor system.
Air inlet collector with opening from top.
3 fastening points designed to compensate the thermal expansion of the turbine section. First
fastening point is positioned near the first journal bearing designed as fix point. Second and third
fastening points are positioned near second bearing and exhaust gas diffuser.
Turbine type Open circuit
Number of shafts 1
Weight of the turbine rotor 3 t
Weightoftheturbine 17 t
Power mechanical output 18,9 MW
Speed 9.420 1/mm
Length 6.550 mm
Width 2.246 mm
Height 2.700 mm
DLE - Dry combustion system with 8 dry pre-mixed diffusion burn combustion chambers,
diagonal/radial mounting direction with crossfire tubes, double walled design of cobalt alloyed
high temperature material with thermal barrier coating and cover cooling design. Main burners
Integrated pilot system, 2 spark plugs in opposite combustion chambers, 2 air cooled direct flame
detectors. System is to demonstrate latest technology of low
exhaust gas emissions such as NO < 70 mg/Nm3 and CO <= 50 mg/Nm3 in Natural Gas Fuel
operation at full load conditions referring to 15% 02.
Fuel supply system for natural gas with filter, safety shut off valve combination, pressure and
temperature monitoring system, fuel manifold assembly, main gas actuator valve. Pipe material in
Bleed air system for start sequence with bleed control valve and for part load/DLE-operation with
bleed control valve. Piping and flexible tube. Sealing air system with seal air valve, regulator, drain
separator and check valve for use during start/stop sequence only. System requires external
instrument air supply.
Compressor cleaning system for hot- and cold wash, with 8 cleaning nozzles and piping assembly
for cleaning liquid. Approved products are Z0K27 and RMC G-21.
High speed membrane coupling between gas turbine and gear box.
Gear Hitachi-NICO Japan
Rated Power according AGMA 23.000 kW
Input speed 9.420 1/mm
Output speed 1.500 1/mm
Overspeed<2min 111 %
AGMA application factor 1,3
Efficiency 98 %
Oil pump mass flow 1.100 1/mm
Weight 9.500 kg
Three-phase alternating current generator, 10,5 kV / 50 Hz / app. 23.000 kVA in brushless and water cooled construction, with exciting system assembled outside of the generator as well as with integrated voltage control system. Manufacturer Brush (GB). Water Cooling Unit is included.
Base frames with Crane system mounted inside the sound enclosure with lifting tools (2,5t), calculated to assist during inspections. Crane system mounted outside the sound enclosure with lifting tools (1 7t) to assemble or dismantle the main compressor and turbine components is not included.
Air pressure system, exhaust system, motors
Gas warning and fire extinguishing systems
Noise enclosure -Advanced sound pressure level at 80 dB(A) at 1 m of distance of sound enclosure at free field conditions only after final installation.
cooling and combustion air system
Control Cabin with Electrical control system
Filter house and air ducts
Lubricating oil system to the particular supply of the bearings of the gas turbine, the gear and the generator, consists of filters, pumps, valves, pressure and temperature monitoring. Main oil pump mechanically driven with connection at the gear. 400VAC pre/post lube oil pump, 24VDC emergency pump. Tube material of the lube system stainless steel. 5.900 I oil tank integrated in the base frame. Oil type ISO VG 32. Oil tank ventilation operated with separate oil mist separator. Oil cooler system is designed as plate heater radiator. Oil mist separator and Oil cooler are integral parts of filter house and are not included.
Natural Gas H, Natural Gas L, City Gas, GZ 50
0° to 60°C
Low Heat Value (LHV) for DLE combustion
8.360 to 9.795 kcal/Nm³,
35,3 to 41,8 MJ/Nm³
Diameter of Particles
Water and liquid hydrocarbons shall not be contained
< = 0.1 wt % (LHV in kcal/kg/10,300)
< = 30 ppm x (LHV in kcal/kg/10,300)
< = 5 ppm wt.
approx. 5,550 Nm3/h
25 bar (g) ± 0.3 bar
DN 65 PN 40
DN 25, guided to the outside of the building, approx. 1 Nm3 per start/stop sequence
Specification and photos are not contractual and are subject to verification upon inspection
PLEASE BE ADVISED THAT INFORMATION INCLUDED IS CONFIDENTIAL IN NATURE AND IS BASED ON PRE-EXISTING BUSINESS RELATIONSHIP WITH THE LEGAL OWNER OF PROPERTY DESCRIBED HEREIN (IF APPLICABLE). AS SUCH, UPON RECEIPT OF SAID INFORMATION THE RECEIVER ACKNOWLEDGES THAT ANY UNAUTHORIZED CONTACT WITH SAID LEGAL SELLER WILL BE CHARACTERIZED AS A BREACH OF CONFIDENTIALITY AND SAID AGREEMENT MAY BE ENFORCED UNDER EXISTING LAW OR IN EQUITY.
This paper was
prepared by General Equipment Inc.
The paper represents an offer of a partner of General Equipment Inc.
All rights are reserved by and for General Equipment Inc.
All content and ideas of this paper are the property of General Equipment Inc.